Email:email@example.com,Fire Extinguishers/Gas Suppression Equipment Manufacturer:Famous Fire Extinguishers Factory for Export,FM200 Gas Fire Extinguisher Supply.We are famous enterprise with research,production,sales,design.Our products are 100% qualified and perfect service after sale.We will supply professional gas fire extinguisher design and budget to you for free.
1, move the group of seven fluorin propane gas bottle into the cabinet put oneself in another's position, the label is for the front. (be sure to move forward, to prevent the cylinder down).
2, install the nozzle to the cabinet put oneself in another's position at the top of the opening.
3, metal hose ends respectively connected to the nozzle and the container valve air outlet (metal hose with one end of the elbow and container valve link).
4, information feedback device around the ribbons in thread in the metal hose elbow the tighten 1/2 base.
5, pull rod connected to the hoop, will tie in the cabinet put oneself in another's position of beam openings, the front end with T sleeve nut and tighten.
6, the electromagnetic drive device is installed at the top of the container valve.
7, pressure gauge wrapped ribbons installation to the container valve of the pressure gauge.
After 8, fixed installation, if the gauge does not display, it can be behind the pressure gauge is hexagonal nut loose with adjustable wrench counterclockwise 1/8-1/4 turn, make the seal loose core and shows the actual pressure inside the bottle, and then to tighten (prevent slow leak).
9, will signal feedback device, and electromagnetic type drive line connection line access to the corresponding position. (alarm installation is complete wiring)
Note: for the whole project acceptance after the debugging insurance pin pulled out of the bottom of solenoid valve
Previous: No Information